An alternate system runs on the fog or great mist injected into the intake air stream. Although a number of commercial systems can be found, growers can assemble and set up their own system using a ruthless piston pump and fog nozzles. The basic components are proven in Fig. 1. A two-stage system controlled by a two- stage thermostat enables more water to be employed on excessively warm, shiny days. Temperature settings ought to be 5-10°F apart.
Algae development in the pads may become a problem that will decrease the effectiveness of the machine and lead to accelerated deterioration of the pads. The addition of an algaecide to the drinking water supply can help in control.
It really is desirable, especially in hard drinking water areas, to add a wetting agent to the drinking water to obtain additional uniform wetting of the pads. A commercial materials or liquid home detergent at the price of 2 tablespoons per 100 gallons may be used.
Water for the pads ought to be clean and lower in mineral content to prevent clogging and coating of the pads. A pump, pipes and gutters are used to recirculate the drinking water. A flow rate 113 gallon per minute per linear foot of pad system ought to be provided to make sure adequate wetting.
In the most common cooling system (fan and pad), the fans draw air through wet pads that expand the length of 1 endwall or sidewall. Aspen and coated cellulose are common pad materials that usually have life of 1 to three years. Approximately one sq . foot of pad are is necessary for 20 square ft of floor area.
Visit our site to discover our approaches behind Greenhouse Exhaust Fan.